We have several options to integrate with BMS:
ModBus port RS 485: RS-485, also known as EIA-485, is a communication standard in bus. Each device intended to communicate using Modbus is given a unique address. Master devices send a command in a frame which contains the address of the device or the end-devices (slaves). All devices are sent the frame, but only the recipient interprets and executes the command. Modbus commands contain checksum information, to allow the recipient to detect transmission errors.
This port is already integrated in our main board, so no extra devide is needed to be purchased.
Lutron gateway: With our dedicated Lutron Gateway Lutron you can control systems on Airzone systems through the Lutron HomeWorks QS Processor. This gateway will allow to:
- Reading/Writing of the room temperature.
- Reading/Writing of the set-point temperature.
- Reading/Writing of the operating mode.
- Reading/Writing of the cooling/heating demand.
- Reading/Writing of the fan speeds.
Lutron manual can be found here
BACnet gateway: Our BACnet Interface Board allows a Building Management System to control all variables of the Airzone systems. The BACnet interface uses a standard open protocol based on ASHRAE Standard 135, and its objects are compatible with: BACnet (ANSI /ASHRAE-135) and BACnet/IP (ISO16484-5)